MATEC Web Conf.
Volume 277, 20192018 International Joint Conference on Metallurgical and Materials Engineering (JCMME 2018)
|Number of page(s)||9|
|Section||Material and Mechanics|
|Published online||02 April 2019|
Replacement of several single function generator protection relay at Badak LNG
Lead Electrical Engineer, Technical Department, Badak LNG, Indonesia
* Corresponding author: firstname.lastname@example.org
Badak LNG is a company that operates the largest LNG Plant in Indonesia with maximum production capacity of 22.5 MTPA. The company operates twelve (12) steam turbine generators and one gas turbine generator and one diesel engine generator to supply electricity for process, utility, storage, loading and plant support facility areas, which constitutes the criticality of power generator equipment to keep the reliability of production process. Generator protection relay is one of the equipment that monitors and protects the generator from fault resulting from either internal or external disturbance, preventing the generator from serious damages. Before 2015, Badak LNG used single function relays to protect the generators. The generators are protected by stator differential protection (87), current unbalance (46), loss of excitation (40), reverse power (32), time overcurrent with voltage restraint (51V), and time overcurrent ground (51G). These single function relays wield more disadvantages compared to the newer technology held by the digital relays. Since 2015, Badak LNG have started to replace the single function generator protection relays with the digital type ones.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.