MATEC Web of Conferences
Volume 54, 20162016 7th International Conference on Mechanical, Industrial, and Manufacturing Technologies (MIMT 2016)
|Number of page(s)||5|
|Section||Automation and control engineering|
|Published online||22 April 2016|
Improving Efficiency and Reliability of Protection System of Tarbela Power Station
1 Student of Centre of Energy system NUST University, Islamabad, Pakistan
2 Lecturer in Centre of Energy System NUST University, Islamabad, Pakistan
Protective relaying system plays a vital role in ensuring the proper and smooth functioning of the Power plant. As the generator is the most expensive part of the plant that’s why the provision of a healthy protection system is must. Protection system guarantees the reliability and safe operation of the plant and is called the brain of the power system. Tarbela is the largest power plant of Pakistan and considered as a back bone of power system of Pakistan. In this paper, the generator protective relay of Tarbela power plant is tested and their results are presented. All the protective relays of Tarbela Power Plant are of electromechanical types which were manufactured in 1970-80. Setting, calculation and test result of these relays were then analyzed and recommendation is made for improving the reliability of the protection system of the said plant. Features of new numerical relays and comparison with the installed relays are also presented and finally the description of upgradation/retrofitting of installed electromechanical relay are discussed for smooth transition to new technology.
© Owned by the authors, published by EDP Sciences, 2016
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.