MATEC Web Conf.
Volume 290, 20199th International Conference on Manufacturing Science and Education – MSE 2019 “Trends in New Industrial Revolution”
|Number of page(s)||10|
|Section||Safety and Health at Work|
|Published online||21 August 2019|
Modelling of noise reduction for Datacentre buildings fire protection with inert gas systems
1 SAFETY RULES SRL, Str. Lt. Gheorghe Saidac 11, Sector 6, Bucharest, Romania
2 Ecological University of Bucharest, Faculty of Management Engineering, Bd. Vasile Milea 1G, Sector 6, Bucharest, Romania
* Corresponding author: firstname.lastname@example.org
Regarding INERGEN Clean gas Total Flood Fire Suppression System, these systems are specifically engineered for total flooding application in either unoccupied or occupied areas, but against its design, or their proved long term efficiency and global scale usage, since INERGEN agent is stored as a gas, it discharges as an invisible gas that can have a more destroying impact than the fire itself. Since 2008 up to now, there have been recorded on yearly basis several reports about INERGEN gas discharges conducting to faults in hard discs (HDD) operating in Data Centres protected by such a solution from fire due to the level of noise produced. The paper shows an analysis of this problem as hard disks damaging source detection and optimization by modelling of nozzle placement in the space choice as a technical solution to avoid these fire extinguisher side effects.
© The Authors, published by EDP Sciences, 2019
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.