MATEC Web Conf.
Volume 197, 2018The 3rd Annual Applied Science and Engineering Conference (AASEC 2018)
|Number of page(s)||6|
|Published online||12 September 2018|
Investigation of transformer failure in Indonesia
PLN Research Institute, Transmission and Distribution Department, Jakarta
* Corresponding author: firstname.lastname@example.org
Transformer failure investigation is important to obtain necessary actions which prevent similar failure from happening in the future. An investigation was conducted upon the failure of a transformer in Indonesia which damaged substation apparatuses nearby. To determine possible cause of the failure, the investigation was performed by doing visual inspection after failure, further analysis on related historical assessment result data and simulation using related nameplate and actual configuration. Most historical assessment result data showed no early failure indication of the transformer, while sweep frequency response analysis (SFRA) test result showed severe deformation on both primary and secondary winding. A simulation using Transient Analysis Program for internal short circuit between winding and ground was conducted and the output waveform was identical to Digital Fault Recorder (DFR) waveform data during transformer failure. Therefore, the possible cause of transformer failure was internal arcing on primary winding to ground which could not be interrupted by the protection system. According to visual inspection after failure, the possible cause of protection system malfunction was accidental open circuit in Current Transformer (CT) secondary circuit which damaged whole CT wiring.
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.