MATEC Web Conf.
Volume 228, 20182018 3rd International Conference on Circuits and Systems (CAS 2018)
|Number of page(s)||4|
|Section||Physics and Materials Engineering|
|Published online||14 November 2018|
Application of the Coordination Control Strategy of pH and SO2 Concentration in the Desulphurization Slurry Supply
Shandong Branch of Huadian Electric Power Research Institute, Jinan, China
2 Huadian International Power Co., Ltd. Zouxian Power Plant Jining, China
a Baoying Zhu: firstname.lastname@example.org
The desulphurization slurry flow of the coal-fired unit is usually regulated by a single PID loop that controls the pH value of the gypsum slurry. And the desulphurization system is characterized with large inertia and serious hysteresis, which often results in SO2 concentration of the outlet exceeding the standard, and leads the operators to turn the regulating valve to manual mode. The SO2 concentration of the outlet was taken into consideration into the optimized control strategy of desulphurization slurry supply introduced in this paper, and it is with the gypsum slurry pH value for cooperative control of the slurry regulating valve. Finally, the experiment proved that after the optimization of the control strategy, the desulfurization loop could be automatically put into operation for a long time, and the SO2 concentration of the outlet keeps stable, and the comprehensive utilization rate of limestone and the automation level of auxiliary equipment are significantly improved.
© The Authors, published by EDP Sciences, 2018
This is an open access article distributed under the terms of the Creative Commons Attribution License 4.0 (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.