MATEC Web Conf.
Volume 173, 20182018 International Conference on Smart Materials, Intelligent Manufacturing and Automation (SMIMA 2018)
|Number of page(s)||5|
|Section||Automation and Nontraditional Manufacturing|
|Published online||19 June 2018|
Analysis of a Dry-type Reactor Fault Based on COMSOL Thermal Field Simulation and High Frequency Pulse Oscillations
Guangzhou Bureau, CSG EHV Power Transmission Company, Guangzhou 510663, China
Corresponding author : firstname.lastname@example.org
For a single-phase earth fault of 35 kV dry-type reactor, the 5th package area is found with serious turn-to-turn short circuit after it conducts the DC resistance test, turn-to-turn insulation test of high frequency oscillation pulse and rework disassembly. The turn-to-turn short circuit of resistance will lead to wire fusing, which makes the conventional pre-test projects have limitations. With COMSOL finite element thermal field simulation of the fault 35kV dry-type reactor, the temperature distribution result of the reactor indicates that the hottest point is at the 6th package during the reactor operation and the temperature rises 73.75K. In addition, the temperature rises of the 5th, 7th, 14th, 15th package is also higher than other packages, which easily causes device failure due to insulation deterioration. Through the analysis and thermal field simulation of the test for failed reactor, it can provide the reference basis for equipment design, manufacture, daily repair and maintenance.
© The Authors, published by EDP Sciences, 2018
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.