MATEC Web Conf.
Volume 330, 2020International Conference on Materials & Energy (ICOME’19)
|Number of page(s)||8|
|Published online||01 December 2020|
Modelling and simulation of a cold storage room driven by a continuous adsorption refrigerator
1 Université de Lorraine, CNRS, LEMTA, F-54000 Nancy, France
2 Gabès University, Energy, water, Environment & Processes (LR18ES35) laboratory, ENIG, Gabès, Tunisia
3 Université de Lorraine, INRA LERMAB, F-54400 Longwy, France
* Corresponding author: email@example.com
The present work proposes a continuous solar adsorption refrigerator for a positive cold storage room of 231 m3 used for fruits and vegetables preservation and installed in the south of Tunisia. After the estimation of the storage room cooling load, which is equal to 13 kW, a parametric study, aims to improve, the performance of the chiller is done in order to achieve the storage room need and to estimate the required heat in the refrigerator generator. A theoretical model, based on the thermodynamics of the adsorption process, heat and mass transfer within the porous medium and energy balance in the system components, is developed and a simulation with Matlab/Simulink, is carried out. The model was established and validated with the literature experimental data. A maximum coefficient of performance of 0.52 and cooling load of 22 kW are reached at cycle time of 800 seconds, the inlet temperatures of heating, cooling and chilled water are 85°C, 22°C and 15°C, respectively.
© The Authors, published by EDP Sciences, 2020
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.