MATEC Web Conf.
Volume 91, 2017The Fourth International Youth Forum “Smart Grids 2016”
|Number of page(s)||4|
|Published online||20 December 2016|
Method of Calculation of Current of the Ground Faults in the Parallel Overhead Transmission Lines 110-220 Kv
1 Platov South State Federal Polytechnic University (NPI), 346428 Novocherkassk, Russia
2 AvtomaticaDon, 347900 Taganrog, Russia
* Corresponding author: email@example.com
The mutual induction between the phase wires of the different overhead lines which situate close to each other cause unbalanced redistribution of currents in the line wires. This leads to emergence of the outof-balance zero sequence current which affects negatively on the sensitivity of the zero-sequence current protection. It is impossible to estimate such out-ofbalance current by the means of the typical calculation programs for short circuit currents. This paper describes the method of “virtual” lines for an extra correction of the values of zero-sequence currents during the current ground faults happening in the overhead lines 110-220 kV. There is an example of using this method for three parallel overhead lines 220 kV passing close to each other.
© The Authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.