Research on Line Patrol Strategy of 110kV Transmission Line after Lightning Strike
1 Guangdong Power Grid Limited Liability Company, Jiangmen Power Supply Bureau, Jiangmen, 529000, China
2 Wuhan Sunshine Power Science & Technology co., LTD, Wuhan, 430074, China
a Corresponding author: email@example.com
Lightning faults occupy in the majority of instantaneous fault and reclosing can usually be successful, so power supply can be restored without immediate patrol in many cases. Firstly, this paper introduces the lightning fault positioning and identifying method. Then test electrical performance of insulators after lightning strike from 110kV lines. Data shows that lightning strike has little effect on the electric performance of insulator. Finally, illustrating disposal process of the 110 kV transmission line after lightning fault, certifying that the power supply reliability be ensured without line patrol.
© Owned by the authors, published by EDP Sciences, 2016
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.